The floor controller sistema LGATE952 provides all relevant data points of the room automation grouped room by room as BACnet objects for the connection of a management system. The compatibility with other components ensures certification as a BACnet Building Controller (B-BC). All BACnet functions of the AMEV profile AS-A are fulfilled.
The easiest possible access to the data points is ensured by clear names and descriptions and by a unique assignment of the BACnet instance numbers.
Preconfigured programs are available for up to 60 rooms with lighting, sun protection and room temperature control. In addition, there are timer programs for energy level switching and presence control as well as data points for central functions and transfer to the system technology, e.g. for optimising the flow temperature or a ventilation system.
For each room the following data are available as BACnet data point:
The following BACnet objects are available for central functions:
The device allows a connection to a LON network via LON/IP-852 or TP/FT-10. The connection to a BACnet network is possible via BACnet/IP or BACnet MS/TP.
|Port 1 10/100 Base-T
Port 2 10/100 Base-T
Port 3 TP/FT-10 (FTT10)
|BACnet objects 1000
BACnet trend logs 512
BACnet not. class obj. 32
LON network var. 2000
|9-35V DC, 12-24V AC 50/60Hz
|(HxWxD) 90(45) x 157 x 60mm
|DIN rail mounting